Customer / Contact person information
Please select the application type. Continuation application requires that the product’s composition and method of manufacturing has not changed during the first 3-year classification period. Additional information about different application types and documentation required can be found here »
The applicant shall pay Building Information Ltd the valid classification fee and any other fees related to the granting of the classification.
Classification fees »
Either GTIN (EAN) or manufacturer's product code is required. If the product is associated with multiple codes, please enter codes using semicolon (;) as separator (e.g. 1234567890123;9876543210321).
Talo 2000 Classification
Pleas, select atleast one language.
Manufacturers own advice / query on meeting the requisitions (in separate attachment).
Read the following sections and approve them by checking a box.
Any insulation materials that are placed inside the duct fulfil the requirements set for fireproof building materials and requirements in accordance with combustibility Sh1 and fire spread class Pll 1 (B-s1,d0) (RakMK E1).The ducts, duct parts, dampers and fire dampers, as well as the access doors and hatches, can be cleaned in accordance with the Finnish construction regulations or type approval instructions and the SFS-EN 12097 standard.No stickers or any with adhesive affixed labels are attached onto the internal surfaces of productsThe ducts and duct parts endure at least 10 cleaning cycles without their structure being damaged. The highest acceptable amount of fibers in the air passing the duct stays under or equal to 0.01 piece/cm3 during and after cleaning (Cleanliness testing instructions for ventilation products 2000).The dampers, valves and fire shutters do not prevent the cleaning of the ducts. It is possible to readjust them to their original position after cleaning. It is possible to check the position of the dampers without opening the channel.The internal surface of the products does not enhance the accumulation of impurities. The roughness of the duct material is less than 1 mm. The joints of the ducts with diameter 200 mm or less and their connecting pieces do not arise more than 2 mm of the ducts inside surface. The joints of the ducts of diameter 315 mm or more and their connecting pieces do not arise more than 3 mm of the ducts inside surface. The products do not have burrs that could complicate cleaning or damage the cleaning equipment.The products fulfil the airtightness requirements of class C of the SFS 4699 standard.The sealants do not emit any substances into the air flow that may cause poor air quality or pose health risks.Classified products are labelled in a recognizable way and can be easily separated from the not classified products. The marking can endure transportation, storage and handling of the products on construction sites.The inside sufaces of the products are protected from contamination during factory storage and transport by sealing the ends of the ducts or packing the parts in closed containers and protecting the load e.g. by covering. The techniques used for protection (such as plugs) and the storage containers are of a type that can withstand the prevailing conditions during transport and on construction sites, as well as being repeatedly opened and closed. If the ducts are transported inside each other, the cleanness of their external surfaces must correspond to their internal surfaces. Product-specific transportation, storage, installation and maintainance instructions are issued and the instructions cover essential information related to cleanness.
Attach the required reports according to the Cleanliness classification testing instructions to your application. Note also the special requirements.