The M1-label marks a product, which has been tested in neutral third-party laboratory and which under the test conditions fulfills the M1-certification criteria. In M1-classification limit values are set for the chemical emission and odour deriving from the product in to the indoor air.
The only criteria concerning the substance content of building materials is set for leveling compounds, putties, screeds, mortars, fillers and plasters. These type of products must be free of casein. Fungicide treatment of fabrics or padding is not allowed in M1-certified products.
The classification sets requirements for building materials, fixture and furniture in office and residential buildings with respect to good indoor air quality.
There is another set of criteria for upholstered office chairs, which has some minor difference with the criteria for building material and furniture with hard surfaces.
Wood, glass, metal, stone and ceramic products have a special status
The document “Classification of Indoor Environment 2018 ” places no restrictions on the use of following products:
- natural stone
- ceramic tile
and construction board and log surfaces made of unprocessed wood (excluding hardwood). The VOC emissions of fresh wood may nevertheless exceed the limit value of emission class M1.
However the classification is not granted for products without test results. If a company wants to use the M1-label on its product, the product must always be tested and an application made.
M1 limit values
|The emission of total volatile organic compounds|
(TVOC) [mg/ m2h]
|< 0,2||< 0,4|
|Emission of a single volatile organic compound (VOC) [µg/m3]||≤ EU-LCI||≤ EU-LCI|
|Formaldehyde emission [mg/ m2h]||< 0,05||< 0,125|
|Ammonium emission [mg/ m2h]||< 0,03||< 0,06|
|The emission of CMR-compounds belonging to category 1A or 1B in Annex VI to Regulation (EC) No 1272/2008 [mg/m3] 1||< 0,001||< 0,001|
|Odour 2||not odorouss||not odorouss|
1) does not include formaldehyde , 2) odour acceptance ≥ 0,0
The emissions of the products falling into the category small areas (2m2) and very small areas (0,4m2) can be assessed also as model room concentrations. The M1-limit values (mg/m3) for such products are: TVOC 0.02, formaldehyde and ammonia 0.01 and CMR-compounds 0,001, single VOC (µg/m3) ≤ EU-LCI, the product shall not be odorous.
Products in category small areas are e.g. doors, windows, wooden beams and tiling grout and very small areas e.g. sealants ans some adhesives .
M1-limit values for office chairs
| The emission of total volatile organic compounds|
|Emission of a single volatile organic compound (VOC) [µg/m3]||≤ EU-LCI /≤ 10|
|Formaldehyde emission [µg/m3]||< 10|
|Ammonium emission [µg/m3]||< 10|
|The emission of CMR-compounds belonging to category 1A or 1B in Annex VI to Regulation (EC) No 1272/2008 [mg/m3] 1||< 1|
|Odour 2||not odorouss|
1) does not apply for formaldehyde , 2) odour acceptance ≥ 0,0
The classified product can be upholstered either with textile or artificial leather. The chairs are group to product groups according their surface material. The grouping is always verified in the technical working group, which also select the products to tested.
In office chairs classification the emission are measured after three days ageing period.
- Fungicide treatment of the chairs fabric/surface material is prohibited
- LCI-values µg/m3, see. EU-LCI Values.
- The assembly date of the chair must be reported, newly manufactured components must be used
Classified products must be applied and maintained according to manufacturers’ instructions
M1-criteria does not include any requirements for emissions during installation. Issues related to occupational health and safety must be checked from the manufacturer’s instructions and Material Safety Data Sheets if available. Classified products must be applied on sites and under the conditions they are designed for. For example, products designed for dry areas must not be used in wet areas.
Furthermore, wrong maintenance practices may lead to deterioration of materials and degeneration of the indoor air quality. Instructions for installation and use of products can be obtained directly from manufacturers and retailers. Design and implementation mistakes of structural elements or ventilation systems cannot be compensated by using low-emission building materials.